Clean Tower Separator System Installation
Side Stream Installations
In addition to being the ideal solution for the removal of solids from a tower basin or sump, the Wingert Clean Tower Separator System may be installed in a side stream, as shown in the illustrations below. Side stream installations are typically sized for 10 - 20% of the main system flow rate (see side stream sizing chart).
|Side Stream Installation with Return to Pump Suction|
The preferred method for side stream cleaning is achieved by installing the separator system across the recirculation pump. This type of installation allows for maximum pressure drop through the separator. The diagram to the right depicts this type of installation.
|Side Stream Installation with Return to Main Line|
Another acceptable installation is the return to the system flow line. This installation allows only for the pressure drop that the separator system pump can provide. Although this is sufficient for separation, the greater the pressure drop - the better the separation. The diagram to the right depicts this type of installation.
Court Thomas Wingert Representatives can assist you with the selection of equipment best suited to your specific needs. Contact our customer service department by e-mail at firstname.lastname@example.org
or call us Monday through Friday from 7:00 a.m. to 5:00 p.m. PST at (714) 379-5519, or fax us at (714) 379-5549.
Send mail to the
with questions or comments about this web site.
Copyright © 2003 J.L. Wingert Company -
Last modified: 3/24/08